- Common uses for capacitors in HVAC
- The two different types of capacitors used in HVAC
- How capacitors are made
- Rules for replacing a capacitor
- Capacitor safety measures
- Lots of valuable related links to give you a closer look so you will learn more about HVAC
Run Start Capacitors HVAC Motors | Electrical Basics
There are two basic types of motor capacitors most commonly used in HVAC applications today. The run capacitor and the start capacitor. Motor capacitors are used to either increase run efficiency of the motor or to give it an initial start boost in torque to a motor. They are sometimes referred to as motor starter capacitors or power capacitors.
Motor capacitors are only used for single-phase motors that generally see heavy use throughout the HVAC industry. Common applications of single-phase motors which use commonly use run capacitors are air handler blower motors, induced draft or forced draft fan motors on high-efficiency furnaces, condenser fan motors, compressors, and pumps for hot water and chilled water.
Common applications for the start capacitor are generally limited to compressors and only to start the compressor. Typically, when a start capacitor is used, a special relay accompanies it in the circuit to disengage the start capacitor after the compressor motor gets its initial boost in torque from the start capacitor. The most common relay for use in disengaging the start capacitor is the potential relay and the least common is the current relay. Power capacitors or motor start capacitor are also referenced when discussing HVAC capacitors.
Use extreme caution!!!
Run Start Capacitors HVAC Motors - Inside Capacitors
The inside part of capacitors are made up of an insulator between two metal plates. The properties of this metal allow the capacitor to store electrons and the insulator prevents the electrons from flowing from one plate to another. The capacitor, therefore, stores energy in the form of electricity just as a battery would hold a charge of electricity. It is, therefore, necessary to take great care whenever working around capacitors even when the power to the unit has been turned off.
Run Start Capacitors HVAC Motors - Capacitor Specifics
Capacitors are measured or rated according to a microfarad rating. Generally, run capacitors are rated for lower microfarad ratings from 3 microfarads to 50 microfarads. Start capacitors have much higher ranges and can be purchased in sizes all the way up to 800 microfarads. Capacitors also have a voltage rating on them with voltage ranging from 240 volts to 440 volts. It is good practice whenever replacing any electrical components to use an exact replacement. There are rules of thumbs that allow one to use a part that is not an exact replacement which is in a certain range but it is best to use an exact replacement. To check to see if a capacitor is bad, use a capacitance tester to measure the microfarad rating on the capacitor. Compare it with the manufacturers rating. If it is more than ten percent off the microfarad rating on the capacitor replace it. With the Microfarad ratings, it is important to follow the 10 percent rule: that is stay within plus or minus 10 percent of the microfarad rating. With the voltage rating, it is okay to go up on the voltage with the replacement but never down. In other words of you have a capacitor rated for 370 volts that is 25 microfarads if you do not have an exact replacement but one that is 25 microfarads and 440 volts that is an acceptable replacement.
Run Start Capacitors HVAC Motors - Motor Capacitors Conclusion
Additionally, if the motor or compressor fails to start for whatever reason part of the troubleshooting list of things to check will be the capacitor. A bad capacitor can cause a motor to fail and burn up especially when heavy load conditions exist. It is difficult to tell unless you are familiar with capacitors but a capacitor that is bulged out on the top or sides is a bad capacitor. It needs to be replaced. There is always an inherent danger when working on electrical components and especially on capacitors. They will shock you even when the power to the equipment is off. Always have a trained expert HVAC technician check out the equipment. They can diagnose the problem quickly and efficiently and have the system back up in no time. They are also very familiar with all the dangers involved so it will done safely with no injuries.
Other Run & Start Capacitors for HVAC Motors resources can be found here.
Do you have a heat pump instead of an air conditioner? See our comprehensive heat pump category for help with heat pumps:
Furthermore, additional heat pump resources here:
- Heat Pump Troubleshooting.
- Heat Pump Problems
- Heat Pump Sequence of Operation
- Basic Maintenance for Heat Pumps
- How Heat Pumps Work
- Converting and Air Conditioner to a HeatPump
- Heat Pump Breaker Trips
Run Start Capacitors HVAC Motors
Air Conditioner Breaker Trips | Air Conditioner Condensation Water Dripping – Condensate Leaks | Air Conditioning Blower Motor Repair | Air Conditioner Troubleshooting | HVAC Refrigerant Leaks | Fixing a Refrigerant Leak | Air Conditioner Compressor Troubleshooting | Variable Speed ECM Blower Motors | Carrier Gas Furnace Reviews | Burnham Boiler Reviews | Lennox Heat Pump Reviews | Building Automation Systems | Daikin Air Conditioner Reviews | Carrier Gas Furnace Reviews | HVAC Triple Evacuation | Variable Speed ECM Condenser Fan Motors | Run Start Capacitors HVAC Motors | Ohms Law and HVAC | Heat Pump Troubleshooting | Fuel-Gas Code Overview | How To Fix Sweating Copper Pipes | Humidifiers and Comfort | Boiler Circulation Problems