Unit Heater Sequence of Operation – Mechanical rooms have very important equipment that needs to be protected. Often mechanical rooms are not conditioned and subject to outside temperatures and freezing conditions that can freeze piping inside the mechanical. For that reason, mechanical rooms often have unit heaters located there to protect piping and other things that cannot be frozen or subject to freezing conditions. The components and sequence of operation are fairly simple. The main components in a hot water unit heater include a fan, a valve, and of course the piping and coils along with the cabinet. Unit heater sequence of operation can also rely on an automatic control system but it can also be stand alone.
Unit Heater Mechanical Room - Hot Water Unit Heater Sequence of Operation
Each Hot Water Unit Heater shall be controlled by a unit mounted thermostat. Sometimes this will refer to as a wall mounted thermostat. Upon a drop in space temperature below the heating set point of 55° F the fan shall start and the hot water valve shall open. When the temperature rises above the setpoint, the fan shall stop and the valve shall close.
The location of the thermostat is dependent upon the design engineers specifications. Typically it is located on the wall next to the door of the mechanical room especially if the door has access to the outdoors.
The valve is usually located on the piping near the unit heater and is controlled by a thermostat and monitored by the building automation system. Sometimes the unit heater is controlled and monitored by the building automation system so any alarms from the unit heater by the BAS especially in freezing conditions should not be ignored.
Unit Heater Sequence of Operation | Conclusion
Unit heaters can be either electric, gas, infrared, hydronic hot water or steam depending on availability of resources and power. The bottom line, is that unit heaters are needed to protect mechanical rooms from freezing conditions. Everything from boilers to water heaters to other piping systems such as fire sprinkler piping and controls is protected with unit heaters.
Unit Heater Sequence of Operation
Air Conditioner Breaker Trips | Air Conditioner Condensation Water Dripping – Condensate Leaks | Air Conditioning Blower Motor Repair | American Standard Gas Furnace Reviews | Fixing a Refrigerant Leak | Air Conditioner Compressor Troubleshooting | Variable Speed ECM Condenser Fan Motors | Carrier Gas Furnace Reviews | Burnham Boiler Reviews | Lennox Heat Pump Reviews | Troubleshooting Broken Thermostats | York Gas Furnace Reviews | Goodman Air Conditioner Reviews | Building Automation Systems | Daikin Air Conditioner Reviews | Carrier Air Conditioner Reviews | HVAC Triple Evacuation | Variable Speed ECM Condenser Fan Motors | Run Start Capacitors HVAC Motors | Ohms Law and HVAC
Share your HVAC Photos or ask a question about your HVAC System by uploading a photo of it.
HVAC Technical Writer
HVAC Writer | Richard Ashworth is a writer, developer, and proprietor of High Performance HVAC. He is also a licensed Master in the following disciplines: HVAC, Electrician and Gas Fitter. Plying the trades he has worked as an HVAC Technician, a Controls Technician, a Commissioning Engineer, a technical writer, a programmer, and a few other technical jobs related to the mentioned trades.
- Maintenance Procedures
- Operational Procedures
- Commissioning Plans for very large projects
- Functional Test Scripts for HVAC Equipment
- Integrated Test Scripts for HVAC/Electrical Systems
- Sequence of Operations for Mechanical Equipment
- Articles for HVAC
- Experience with retrofit, critical facilities, institutional, and commercial projects.
- I also offer to consult for websites. I do both on-page and off-page SEO to help you get more traffic, therefore, increasing sales.
Anyone need a good HVAC technical writer use the form below to contact. Please include a phone number and best time to call. Thanks!!