Heat Pump Troubleshooting Advice. When you have a problem with your heat pump you want to check the basics. Anything beyond that you really need to call in a professional to troubleshoot the heat pump. The heat pump or any type of electrical mechanical equipment you have problems with and need to troubleshoot. Whether you call for heat pump troubleshooting or any other repair there is only so much you can do.
Heat Pump Troubleshooting Advice
Before calling a heating and air conditioning company, check the following:
- Power Supply
- Ice or Freezing
- Air Flow
- Condenser Fan Motor
A basic description of that list is found below. This is designed to give you the basics of heat pump troubleshooting.
1. Heat Pump Troubleshooting Advice | Thermostat
Check selections on the thermostat. Ensure that it is set to the desired settings. I’ve responded to service calls where the homeowner made a no heat or no cool call. I found they had the thermostat set to heat when they wanted to cool. Or set to cooling when they wanted heat. Additionally, make sure the set point is correct. For example, if you want heating, make sure the thermostat is set to heat. Furthermore, if the temperature in the house is 65° F make sure you turn the thermostat setting up above 65° F. to get heat.
2. Heat Pump Troubleshooting Advice | Power Supply
Check power supply. This can include a circuit breaker and or/a regular looking wall switch close to the unit. This is another easy fix. I have responded to no heat or no cooling calls only to find the power was turned off inadvertently. Perhaps relatives were visiting and someone mistook the wall switch for a light switch. These switches are typically not on heat pumps as a heat pump liking has a breaker next to the heat pump. Make sure you check the breaker at the air handler and the breaker in the main panel. A typical split system will have separate breakers. One for the condenser and one for the air handler.
3. Heat Pump Troubleshooting Advice | Ice or Freezing
In the summer check for freezing up of the heat pump. If the air heat pump unit is frozen turn it off. Check the air filter(s) to make sure they are not clogged or obstructed in any way. In the summer if the evaporator coil has ice on it or any of the copper pipes have ice on them then you have a problem that needs the attention of a professional. If you find no problems leave the unit turned off and call a service company.
In the winter, check the condenser (outside unit) does not have excessive ice on the coils. This could mean the defrost mode isn’t working properly and may need a minor adjustment or a repair altogether. It is best to call a pro to fix that issue.
4. Heat Pump Troubleshooting Advice | Air Flow
Is the air handler blower working good and blowing air out of all of the supply vents? If not or it is weak then you likely have an airflow issue. Always make sure you have a clean filter and that all of your supply vents are open and unobstructed. If this is all good then you have another problem with the airflow. Maybe a bad blower motor, the unit is freezing up inside the evaporator coil or collapsed ductwork. In any of these cases, it is time to call an HVAC repair service. Bad air flow indicates a serious problem.
5. Heat Pump Troubleshooting Advice | Condenser Fan Motor
Is the condenser fan motor turning at the heat pump condenser? Word of note - sometimes in the winter or when you have the heat pump in heating mode the fan will not turn while the compressor is running. This is normal and a part of the automatic defrost mode for the heat pump. If the fan is not turning but you hear the compressor running then something is wrong (unless as noted above with defrost mode) and you need to call a professional.
Heat Pump Troubleshooting Advice | Heat Pump Diagnosis & Repair
Additional Helpful Troubleshooting Hints
- Always change your filter on a monthly basis
- Make sure all your supply vents are open and unobstructed
- Keep area clean around indoor unit especially the return grills
- Keep outdoor condensing units free of leaves, grass, and debris including trash cans and/or children’s toys or playthings like small plastic pools or playhouses. Additionally, your service technician will appreciate you not planting holly bushes near the outside unit
- Have air conditioner, heat pump, or furnace system serviced every six months
Troubleshooting Heat Pumps Advice Advisory
When you read information on the web double check that the information is correct.
I read this directly from an un-named article on the internet that has a number one position in a search for troubleshooting heat pumps – “check the heat pumps ignition”. What? Can you say that one more time? It is obvious to me the person who wrote that article has never touched a heat pump in their life and should have never written an article for troubleshooting heat pumps. Can someone please tell me where the igniter is on a heat pump?
I’ve was out of the field for a year doing management work and now I am doing engineering work and occasionally going out to the field but I do not think the basic concept of heat pumps has changed that much to include adding ignition systems to heat pumps. If you are going to troubleshoot your own heat pump then please follow the basics above. Beyond that please call a professional to repair your heat pump or troubleshoot your air conditioner.
Turning Faulty Advice into Good Advice
Some other faulty advice from around the web:
Heat Pump Troubleshooting Advice – “Most of the time when your heat pump doesn’t work it is a faulty thermostat”. I’ve been on many service calls and I have found faulty thermostats. Most of the time the reason for a faulty thermostat is because the homeowner thought the thermostat was bad and the decided to change it. Changing parts, especially the thermostat, simply doesn’t work most of the time.
Whatever reason the homeowner didn’t wire it properly or they didn’t turn the power off and crossed the wrong wires and burned up the heating anticipator or blew the transformer. Unless you have had a lightening strike, major power surge that took out other electronic devices in your home, or someone took a hammer to the thermostat then your problem is probably not the thermostat. If you have problems with your heat pump or air conditioner and want to troubleshoot the problem yourself simply check the settings of the thermostat. Make sure it is set to the appropriate setting. Double check to make sure it is set to the appropriate setting.
Parts Changers Rarely Make the Repair | Heat Pump Troubleshooting
If everything is correct then you are done at the thermostat. Don’t run down to your local hardware store and buy a new thermostat for your heat pump thinking it will solve the problem. Chances are, if you doing it as a part of the process of finding the problem with your heat pump then you will probably still be cold after changing the thermostat in the process of troubleshooting a heat pump. You can change every single part in the heat pump system and still have a problem with the heat pump. Furthermore, changing parts, especially the thermostat, simply doesn’t work most of the time.
Blower Motors | Heat Pump Troubleshooting
Heat Pump Troubleshooting Advice – “The motor may need to be reset” is another thing that struck me from reading this article for troubleshoot heat pumps – Reset the motor? I have not seen many blower motors that have a reset button on them. There are very few out there that have reset buttons on the blower motor but chances are you do not have the type of motor that has a reset button on it.
It seems to me the person who wrote this article read an article on oil furnaces or boilers and tried to adapt it to troubleshooting heat pumps. Oil burners have reset buttons on them but not on the blower – the reset button is on the burner as a part of the burner ignition controls. If there are any manual reset buttons on heat pump it is possible there is a manual reset button on the condensing unit. Furthermore, I know of only two manufacturers that have these reset buttons on their heat pumps. Rheem and Ruud.
To Reset or Not to Reset | Heat Pump Troubleshooting
This is not a reset button for any motor but a high pressure reset switch. If this switch needs to be reset on a heat pump it means the head pressure or the high pressure side of the heat pump is exceeding maximum pressure and is killing the unit as it should to avoid damaging the compressor or other components in the refrigeration loop of the heat pump. This means one of several reasons if you are repairing the heat pump. Furthermore, the condenser coils are plugged up with trash, dirt, or other debris like grass, the condenser fan motor has failed, or there is a refrigeration problem such as an over charge of refrigerant in the system.
Circuit Breakers | Heat Pump Troubleshooting
Heat Pump Troubleshooting Advice – “Heat Pump trips the circuit breaker” – they tell you to check the heat pump circuit breaker in this bad article. Which heat pump breaker do I check? A real heat pump has two circuit breakers in the circuit breaker panel for the home and if the heat pump has electric back up heat then it should have another set of breakers or fuse protection at the location where the heat strips are which is usually in the air handler.
Yes, a real heat pump (not the fictional dream heat pump they describe in this heat pump repair article) has two circuit breakers. One for the heat pump condenser and one for the air handler. If the breakers are tripping on the heat pump circuit then you have a dead short somewhere in the system and it needs to be addressed by a professional.
Air Handlers | Heat Pump Troubleshooting
“Air Handler Squeals” – they tell you that it is usually the belt. Huh? In the residential market HVAC manufacturers went to direct drive blowers many, many moons ago and stopped distributing units that are belt driven. 99.9% of heat pump air handlers out there installed in homes are direct drive. Finding a belt driven blower in residential systems is akin to to finding a Model T. If your heat pump this old it is time to replace the system and not the belt.
Heat Pump Troubleshooting Advice | Heat Pump Diagnosis & Repair - Conclusion
Okay, I’m done commenting on that bad article for finding and fixing a problem heat pumps. Some of the information in that article is okay although general knowledge. If troubleshooting heat pumps is your profession please go ahead and fix it. Chances are you are not a professional HVAC technician so please check the basics. Furthermore, leave it up to the professional HVAC Technician to troubleshoot the heat pump.
High Performance HVAC Heat Pump Troubleshooting and Repair Advice
Air Conditioner Breaker Trips | Air Conditioner Condensation Water Dripping – Condensate Leaks | Air Conditioning Blower Motor Repair | Air Conditioner Troubleshooting | Fixing a Refrigerant Leak Air Conditioner Compressor Troubleshooting | Variable Speed ECM Blower Motors | Carrier Gas Furnace Reviews | Burnham Boiler Reviews | Lennox Heat Pump Reviews | Building Automation Systems | Daikin Air Conditioner Reviews | HVAC Triple Evacuation | Variable Speed ECM Condenser Fan Motors | Ohms Law and HVAC | Condenser Fan Motor Repair | Fuel-Gas Code Overview | How To Fix Sweating Copper Pipes | Humidifiers and Comfort | Boiler Circulation Problems | Troubleshooting Broken Thermostats
Share your HVAC Photos or ask a question about your HVAC System by uploading a photo of it.