- A basic troubleshooting list of things that cause high head pressure
- Condenser Fan Motors
- Condensing Units and Condenser Coils
- The Line set and basic devices in the line set
- Non-condensing gases in the system
- Refrigerant overcharge
- Design conditions and head pressure
High Head Pressure Air Conditioner Heat Pump
Condenser Fan Motor
When first encountering the problem of high head pressure it is important to check the basics first. The condenser fan motor and the condenser coils are the most common problems I have found with the issue of high head pressure. Of course there are other issues that can cause high head pressure but these are the most common. In one case, the condenser fan motor appeared to be working find but through the process of troubleshooting I did an RPM check of the condenser fan motor and found it to be turning at 900 RPM’s. Almost 200 RPM’s lower than what it was supposed to be turning.
I know all technicians do not carrying an RPM gauge tester but I have found it very useful in a lot of cases where the problem seemed to be mysterious. Use an RPM meter solved some of those mystery’s especially with fan motors and pumps that are required to turn at a specific RPM. The RPM meter I carried required reflective tape to be applied as close to the motor shaft as possible. There are other types of RPM meters but the one with reflective tape is the one I have always had luck with.
Condenser Coils | High Head Pressure Air Conditioner Heat Pump
Plugged up condenser coils is another big problem commonly encountered with high head pressure. This is also probably the easiest one to solve provided you have a water hose nearby. A little coil cleaner and spraying water (from the inside out) will solve that problem and drop the head pressure to normal levels. I usually advise the homeowners to turn off their air conditioner or heat pump when they are cutting the grass. By following that advice, it keeps a lot of grass out of the air conditioner or heat pump condenser coils. Therefore, they do not have that problem of grass plugging up the coils. Simply make sure the condensing unit stays as clean as possible and you can avoid this problem.
Other problems that can result in high head pressure from condenser coils is corroded coils. This can happen as a result of living near the coast (environmental issues with the air) and/or animal urine. I had a call from a residential customer with this problem. It seems their dog thought the condenser was a fire hydrant and constantly did his business on the condenser. The condenser lost and the corroded coils caused the high head pressure. Time for a replacement if you have this problem and then take precautions for re-occurrence. Manufacturers typically have a salt spray rating on their condensers. Choose the best rating for coastal areas and then purchase a special spray to spray the coils before putting into service. If its an animal problem build a fence around the unit.
Restriction in the Line Set | High Head Pressure Air Conditioner Heat Pump
If you have a high hear pressure in a condenser and the fan motor is working fine and the coils are clean then you need to go hunting. Check all your filter driers. Some filter driers have pressure access ports on them so you can see if the filter is plugged using your gauges. Other filter driers without the pressure access ports need to be checked by temperature. Using an infrared temperature gun is not always the best method in this case as infrared’s do not work very well on copper. I use a digital thermometer that has individual probes. The readout will give me the differential temperature. Usually a few degrees is okay but when you get a larger number for a differential temperature from one side of the filter drier to the other then you have a restriction and you need to replace the filter drier.
Other restrictions can be the metering device getting plugged up with debris. I have found both the piston type and the TXV type with restrictions that caused high head pressure. In one case I found a bead of solder was restricting the piston. That was from improper soldering methods namely using too much solder. Another case was a TXV. Once I found the TXV it was frosted. Replaced the TXV and the system returned to normal operation. Crimped copper lines can also cause restrictions. The satellite TV installer crushed the liquid line in an attic in one case and the other case was unknown how it happened but it was crimped and causing high head pressure.
Non-Condensing Gases in the Refrigeration System | High Head Pressure Air Conditioner Heat Pump
In this particular case the homeowner installed the system themselves. It was one of those purchased online deals. They purchased the unit online and decided to install it themselves to save money. They did a decent job with most of it except when it came to the refrigeration part they were clueless. They must have read the instructions to a certain point and then ignored the rest of it. No vacuum was pulled. The simply soldered it up, hooked up the wiring, and put the charge to it. The pressures were fluctuating wildly. At first they were pretty good at playing dumb but then the wife fessed up and told me what they did. I recovered everything out of the system, did a proper triple evacuation, and recharged. Everything went back to normal. In most cases I give the homeowner a warranty on my work. In this case I did not. I never heard from them again so I am guessing it went well for them.
How can you tell there is non-condensing gases in the the system? The pressures will fluctuate wildly giving you a definite high head pressure reading. That is at least from my experience. Has the system been accessed recently by someone? Is it a new installation? Hopefully, the homeowner will fess up like mine did when I found the non-condensing gases problem and you will be able to solve the problem much quicker.
Refrigerant Overcharge | High Head Pressure Air Conditioner Heat Pump
This happens quite frequently even with HVAC technicians. They do not use the proper procedures when charging the system. Using a chart, collecting basic data such as indoor wet bulb, outdoor dry bulb, and using the pressures to properly charge the unit is a necessity. Otherwise you are just guessing. Using the proper superheat or subcooling methods to charge a unit are absolutely essential at getting it right the first time. I’ve hear customers say, “I think I need some more Freon to make it colder”. They don’t understand that adding more Freon in properly charge system will make it not colder. The system will use more power and not cool as effectively. Hit that sweet spot on your superheat or subcooling chart and everyone will be happy and you can avoid high head pressure in the system.
Conclusion | High Head Pressure Air Conditioner Heat Pump
Don’t forget design conditions when thinking about high head pressure. Most HVAC systems are designed for a maximum outdoor ambient temperature of 95° F. So if the temperature is at or above 95° with high humidity then you will likely also experience high head pressures. Or at least above normal head pressure for the sir conditioner or heat pump. The system is working hard not only to remove the sensible heat load but also the latent heat load so the pressures will be high in those conditions.
lastly, if you re ever in a situation that is a big mystery and hard to figure out out step back and take a deep breathe. When you return check the basics with a fresh new look. Good luck……….comments are welcome below.
High Head Pressure Air Conditioner Heat Pump
Air Conditioner Breaker Trips | Air Conditioner Condensation Water Dripping – Condensate Leaks | Air Conditioning Blower Motor Repair | Air Conditioner Troubleshooting | HVAC Refrigerant Leaks | Fixing a Refrigerant Leak Air Conditioner Compressor Troubleshooting | Variable Speed ECM Condenser Fan Motors | Burnham Boiler Reviews | Lennox Heat Pump Reviews | Troubleshooting Broken Thermostats | Building Automation Systems | Daikin Air Conditioner Reviews | HVAC Triple Evacuation | Variable Speed ECM Condenser Fan Motors | Ohms Law and HVAC | R-134A PT Chart |
Share your HVAC Photos or ask a question about your HVAC System by uploading a photo of it.