Gas valves used in a modern state of the art residential gas furnaces are typically controlled via a state of the art electronic ignition control or a printed circuit board. Other types of gas valves include the standing pilot gas valve. Gas valves can be found on gas furnaces, gas fired steam boilers or hot water boilers, and gas-fired water heaters. When troubleshooting a gas valve the technician should only be concerned with input to the gas valve and output of the gas valve. Whether it is an electronic module or circuit board controlled gas valve or a standing pilot gas valve.
Gas Valve Troubleshooting | Electronic Ignition Gas Valve Troubleshooting
If something is wrong with the internal components of the gas valve the gas valve should be replaced. The gas valve cannot be repaired in the field. Only the gas valve manufacturer or someone certified by the manufacturer of the gas valve can make repairs. Then recertifying the safety of the gas valve. This also applies to gas valves that have been submerged under water due to flooding. Flooding of your boiler or gas furnace or water heater. If the gas valve is found to be defective internally in any way you need a new gas valve. After a gas valve has been submerged or partially submerged replace it a new gas valve.
Gas Valve Troubleshooting | Basics
Any electronic component has a basic troubleshooting rule that every technician should follow when efficiently troubleshooting any electronic ignition gas component. The board should have an input and an output to follow a basic control sequence. The basic control sequence for an electronic ignition control board typically originates at a thermostat for a call for heat. By initiating a call for heat from the thermostat the technician begins the process of the sequence of operation. This completes a circuit to the main control. The electronic control or printed circuit board for the gas furnace. The control sequence of operation for an electronic ignition gas furnace will always include safeties to be proven before the gas electronic control board or printed circuit board allows any output to the gas valve. The safety circuit in many gas furnaces including boilers will include but are not limited to the following:
Components of the Furnace that Work in Conjunction with the Gas Valve
- Forced Draft or Induced Draft Pressure Switch
- Draft hood limit switches
- Limit switches in or near the heat exchanger
- Limit switches near the blower motor
- Any other safety switch that can be opened by temperature or pressure. A switch that is integral to the safety circuit of the gas furnace. Each brand of furnace is engineered differently. See the pictorial or the ladder diagram for all safeties engineered in the gas furnace. These diagrams can be found inside the control of the furnace.
Safeties | Gas Valve Troubleshooting
Once all the safeties are proven the electronic ignition control board will send a signal to the gas valve. The command will be to open either the main valve (if it is direct ignition) or to light the intermittent pilot light. Whether it is direct ignition or intermittent pilot light the flame must be proven through a flame sensor. Proven to keep the sequence from restarting and trying the ignition sequence again. If the flame cannot be proven then the system will shut down for a predetermined amount of time. +/- 4 hours is typical.
If a flame cannot be proven the manufacturer of the controls and the furnace do not want the gas furnace continuously trying for ignition. This is because a dangerous amount of gas can accumulate resulting in serious damage to a structure or people. If the flame is proven the sequence continues until the thermostat is satisfied and everything shuts down until the thermostat again calls for heat and then the whole sequences has to be proven over again so the furnace can provide heat.
Standing Pilot Gas Valve Troubleshooting
Everything that applies to the electronic ignition sequence of operation by the way of the safety circuit must be proven before the gas furnace will allow the gas valve to fire the main burners to provide heat. The difference is the standing pilot gas furnace always has a pilot light on.
Again, if you are not properly trained in the functionality of gas furnaces and basic safety practices you should call a professional. See our disclaimer. Working on HVAC equipment can be hazardous. Call a professional whenever your gas furnace is not working properly.
Gas Furnace Components – Gas Valve Troubleshooting
Resource, Learn More HVAC and About the Author
Air Conditioner Breaker Trips | Air Conditioner Condensation Water Dripping – Condensate Leaks | Air Conditioning Blower Motor Repair | Air Conditioner Troubleshooting | HVAC Refrigerant Leaks | Fixing a Refrigerant Leak | Air Conditioner Compressor Troubleshooting | Variable Speed ECM Condenser Fan Motors | How Expansion Tanks Work | Hot Water Boilers | Boiler Troubleshooting Problems | Boiler Piping Flow & Pipe Sizing | Burnham Boiler Reviews | Lennox Heat Pump Reviews | Troubleshooting Broken Thermostats | Building Automation Systems | Boiler Circulation Problems Troubleshooting | Hot Water Boiler Sequence of Operation | Daikin Air Conditioner Reviews | Heat Pump Thermostat Wiring Chart Diagram |
Share your HVAC Photos or ask a question about your HVAC System by uploading a photo of it.