Gas furnaces types come in a variety of sizes and can be used for different applications. By and large, the most common gas furnaces use natural gas and utilize electronic ignition. Electronic ignition gas furnaces are slowly replacing the older style standing pilot furnaces where a pilot light remained lit all the time. Now, with the newer modern electronic ignition, gas furnaces only use gas when there is an actual call for heat. This adds efficiency because with the older standing pilot gas furnace the pilot remained on even in the summer months. The heat produced by a standing pilot light is negligible. However, it is still added heat to the system in the summer. The whole purpose in the summer is to remove the heat from the system. Rather than add heat like a standing pilot would do.
Gas Furnace Types| HVAC Heating
A gas furnace is rated for efficiency by AFUE or Annual Fuel Utilization Efficiency rating. Furnaces installed before the nineties have efficiency ratings down to 60 percent efficient (or less in some cases). AFUE ratings of gas furnaces are the amount of heat delivered by the furnace divided by the fuel used to make that heat. Another way to look at AFUE is to measure the amount of heat lost up the exhaust stack. If the furnace delivers 90 percent of the heat produced into the dwelling then ten percent of the heat produced is lost up the stack.
Classification of Furnaces
Furnaces can be classified or categorized differently. It really depends on your perspective. Here are different to classify gas furnace types. There is an argument for having a standing pilot gas furnace versus an electronic ignition gas furnace.
- Standing pilot gas furnace. These are slowly being replaced by electronic ignition gas furnaces. Standing pilot gas furnaces use older technology and are not as efficient as the newer more modern electronic ignition cousins.
- Electronic ignition gas furnace. There further classifications of electronic ignition gas furnaces. One way to describe them is the type of electronic ignition they utilize. Among those furnaces, these can be classified as - Direct spark ignition, intermittent pilot, and hot surface ignition. Among these, there are direct fired and indirect fired furnaces. Direct fired happens when the ignition method directly lights the main burner. Indirect happens when a pilot light lights the main burners. The pilot light is lit by electronic ignition.
Further classification of gas furnace types are:
- Single Stage gas furnace
- Two-Stage gas furnace (there are some three stage gas furnaces).
- Modulating gas furnace
Among all furnaces, you can purchase there is an additional classification of gas furnace types. Or you could call it a subcategory:
- Lowboy gas furnaces for installation tight spaces
- Upflow gas furnaces
- Downflow gas furnaces
- Horizontal flow gas furnaces
- Package unit gas furnaces
- Duct heater gas furnaces
- Pool heater gas furnaces
- Unit heaters
- Wall heater gas furnaces
- Floor heater gas furnaces
- Lastly, I have often heard people refer to their boiler as a furnace although technically it is a boiler. A boiler can either be a hot water boiler or a steam boiler within the gas-fired boilers.
Efficiency | Gas Furnace Types
Even the highest AFUE rated furnace is going to lose heat up the stack. It is nearly impossible to get 100 percent AFUE out of any gas or oil furnace. That is because all oil and gas delivered to a furnace have a small amount of moisture in it. You can also expect some jacket losses. Gas typically has a moisture content of 4 to 5 percent. Oil depends on the quality of oil purchased, how many additives used in the oil, and the integrity of the oil tank and piping system. The end result of all this moisture and additives in the fuels affects the AFUE of the furnace and is the reason why no gas or oil furnace can achieve more than 96 percent efficiency.
Gas Furnace Types | The Standing Pilot Gas Furnace
The typical Standing Pilot Gas furnace uses a thermocouple. The thermocouple keeps a flame lit 24 hours a day seven days a week. The pilot light is manually lit and once lit it should remain lit unless a draft blows it out or the thermocouple fails. Thermocouple failure is common but not as common as a draft blowing the pilot light out. Typically, whenever a high wind conditions the wind could extinguish the pilot light. If this happens to you and you are not sure how to relight the pilot light call a professional.
Always follow the manufacturer’s safety guidelines. If you feel comfortable lighting the pilot, carefully do so at your own risk. Remember, both natural gas and propane are flammable and can be explosive given the right conditions. By nature, natural gas is lighter than air and propane is heavier than air. This means that propane will settle in the lowest parts of your dwelling. Natural gas will settle or get trapped in higher parts of the dwelling. Always keep this in mind and if you smell a rotten egg smell then do not light a match or lighter. At least not until the area is safely vented. Many gas-fired water heaters use the standing pilot system.
Gas Furnace Types | The Electronic Ignition Furnace
Electronic ignition gas furnaces are more commonly produced today than standing pilot gas furnaces. They offer added efficiency because these gas furnaces automatically light a pilot when the thermostat calls for heat. The standing pilot gas furnace requires a pilot light to be lit all the time. Most gas and oil furnaces are integrated with the air conditioning system. They make use of the same blower. Additionally, the electronic ignition keeps the heat out of the furnace even in the summer. Therefore, there is less heat to remove by the air conditioning system. The electronic ignition gas furnace is more efficient than standing pilot gas furnaces.
Gas Furnace Types | Gas Fired Unit Heaters
In some applications, it is necessary to use gas-fired unit heaters to heat a space. Gas fired unit heaters can be found in garages, mechanical rooms, electrical closets, and large open spaces. Big spaces in large structures like warehouses, aircraft hangers, or vehicle garages. These gas-fired unit heaters are usually not ducted but they can be adapted to ductwork.
Gas Furnace Types
Air Conditioner Breaker Trips | Air Conditioner Condensation Water Dripping – Condensate Leaks | Air Conditioning Blower Motor Repair | Air Conditioner Troubleshooting | HVAC Refrigerant Leaks | Fixing a Refrigerant Leak | Air Conditioner Compressor Troubleshooting | Variable Speed ECM Condenser Fan Motors | How Expansion Tanks Work | Hot Water Boilers | Boiler Troubleshooting Problems | Boiler Piping Flow & Pipe Sizing | Burnham Boiler Reviews | Lennox Heat Pump Reviews | Troubleshooting Broken Thermostats | Building Automation Systems | Boiler Circulation Problems Troubleshooting | Hot Water Boiler Sequence of Operation | Daikin Air Conditioner Reviews | Heat Pump Thermostat Wiring Chart Diagram |
Share your HVAC Photos or ask a question about your HVAC System by uploading a photo of it.