Evaporator Coil Heat Pumps Air Conditioners – the evaporator is responsible for absorbing heat into the coils and the refrigerant. The evaporator is an essential component of vapor compression refrigeration. This is usually done as result of passing air or water over the evaporator coil where a heat exchange process takes place. Heat leaves the air or water (whatever medium is used) and is absorbed into the coil and the liquid refrigerant. As more and more heat is absorbed by the evaporator coil and the refrigerant again changes state from a liquid to a refrigerant vapor. By the time the refrigerant leaves the evaporator coil the refrigerant should be all vapor and ready to be received again by the refrigeration compressor.
Evaporator Coil Heat Pumps Air Conditioners - Refrigerant Flow & Types
- A coils. These are typically in the shape of an “A”. See the photo below for an example of an A-coil evaporator.
- Slab coils - A slab coil is simply one solid piece of coil. It looks similar to a radiator in your car.
- N-Coil - Basically, the coil looks like an “N”.
Coils for air conditioners and heat pumps can be purchased cased or uncased. In other words, the coil can come in a custom made cabinet or just stand alone coil. Usually, the stand alone coil is purchased to replace an existing coil that is already installed in its own cabinet. A cased coil is also installed in the ductwork near the air handler. This all depends on the installation, the air handler and the configuration.
Evaporator Coil Heat Pumps Air Conditioners | Materials and Maintenance
Coil Materials | Evaporator Coil Heat Pumps Air Conditioners
There are some special order evaporators coils that are all copper. These are normally used in health care facilities. Copper inhibits the growth of mold and mildew, thus the reason why it is used in healthcare facilities. These coils are extremely expensive compared to the typical coils made from copper with aluminum fins.
The refrigerant changes state in the coils. In the evaporator coil the change of state is from a liquid to a vapor while in the condenser the change of state is from a vapor to a liquid. This is all necessary for the process of refrigeration to work properly. The typical evaporator coil is constructed of copper with aluminum fins surrounding the copper coils. The aluminum fins adds surface area to the copper coils and enhances the heat exchange rate making the coils more efficient. Although some manufacturers are switching to all aluminum coils in both the condenser and the air handler evaporator coil. For more on this you can read our article titles aluminum versus copper coils.
Coil Maintenance | Evaporator Coil Heat Pumps Air Conditioners
The best way to maintain evaporator coils is keep a good clean filter in your system. Additionally, it is also a good idea to make sure you have good tight ductwork. Small leaks in the return duct can cause your evaporator coil to load up with dust and dirt. This inhibits airflow and eventually will cause the system to fail. It is essential that the coil gets the designed amount of airflow across the coil for the heat exchange process. Clogged air filters have a detrimental affect on the system also. Furthermore, having no air filter in the system is very bad and WILL lead to failure. Lastly, make sure you take care of your evaporator by keeping a good clean filter in the system.
Finally, for more information on HVAC and heating and cooling use this resource.
Evaporator Coil for Heat Pumps & Air Conditioners
Air Conditioner Breaker Trips | Air Conditioner Condensation Water Dripping – Condensate Leaks | Air Conditioning Blower Motor Repair | Air Conditioner Troubleshooting | HVAC Refrigerant Leaks | Fixing a Refrigerant Leak | Air Conditioner Compressor Troubleshooting | Variable Speed ECM Blower Motors | Carrier Gas Furnace Reviews | Burnham Boiler Reviews | Lennox Heat Pump Reviews | Building Automation Systems | Daikin Air Conditioner Reviews | Carrier Gas Furnace Reviews | HVAC Triple Evacuation | Variable Speed ECM Condenser Fan Motors | Run Start Capacitors HVAC Motors | Ohms Law and HVAC | Heat Pump Troubleshooting | Fuel-Gas Code Overview | How To Fix Sweating Copper Pipes | Humidifiers and Comfort | Boiler Circulation Problems