Table of Contents
Boiler Water Loops - In boiler water loops there are different ways to arrangement the piping depending on the budget at installation time and how efficient and balanced you want the hydronic piping system to be when the job is complete. Some piping arrangements require more pipe upon initial installation. However, they are easier to balance and provide even heat throughout all the radiators or baseboards.
Boiler Water Loops | Hydronic Piping Systems
It is important to consult with a plumbing and heating professional. Consultation should be done before deciding which type of hydronic piping arrangement you want. The type of boiler water loop you will use for your hydronic loop. They can show you the distinct advantages and disadvantages along with cost differences of various hydronic piping arrangements. The piping system you need for the structure where you intend on installing this system. The type of loop can oftentimes be just as important as properly sizing the boiler pipe and system as a whole. It can make all the difference in the world in comfort and efficiency. Consulting a professional will ensure the design is done properly from the start.
One Pipe Series Loop
The One Pipe Series Hydronic Loop uses less pipe than any other hydronic piping arrangement. Therefore it is less expensive to install the piping. However, you need bigger radiators or longer baseboards. However, only at the end of the loop because this part of the boiler water loop will have less heat. The radiators or baseboards at the beginning of the loop use most of the heat. Consequently, this is the reason for the larger radiators and baseboards at the end of the loop. There is also a larger temperature drop in this type of boiler water loop. A temperature drop between the supply and the return versus other types of hydronic piping arrangements. The near boiler piping may need to be modified to prevent large delta T between supply and return.
Monoflow Hydronic Loop and Monoflow Tees
The monoflow hydronic loop is similar to the one pipe series. The exception is the main loop uses monoflow tees to divert the water. It diverts water to the radiators or baseboards using special Tees. The main hydronic loop maintains a constant flow on a call for heat. Using this system, the water temperatures for each zone are more even throughout the hydronic loop. More even than the one pipe series hydronic loop. The monoflow tee is a special tee. The monoflow tee is installed at the supply and the return. The supply and return for each radiator or baseboard.
This boiler water loop system is easy to zone but needs more piping and special monoflow tees for each separate circuit. Additionally, if not installed properly flow problems will occur in radiators and/or baseboards. It is really important if you have a monoflow system to consult a professional before making changes. If you want to modify it in any way for an addition or other work. Always consult a plumbing and heating HVAC specialist for any changes to a monoflow loop.
Two Pipe Direct Return Hydronic Loop
The Two Pipe Direct Return Boiler Water Loop utilizes more pipe than the one pipe series loop. However, all radiators and baseboards receive the same temperature of water, therefore it is more even heat. More even heat than in all the radiators and/or baseboards than the one pipe series loop. Another advantage of two pipe direct return loop over the one pipe series loop is that it can be zoned. Zoning gives you more control over where and when you want heat. This can save you money on the cost of heating. As with many hydronic loop systems the two pipe direct return needs balancing valves. The near boiler piping may need to be modified to prevent large delta T between supply and return.
Two Pipe Reverse Return Hydronic Loop
The Two Pipe Reverse Return Boiler Water Loop uses more pipe than the two pipe direct return hydronic loop. However, the flow is more balanced and even than the two pipe direct return boiler water loop. All baseboards and radiators receive the same temperature of the water so are the same as the two pipe direct return. However, it is an advantage over the one pipe series hydronic loop. Zoning is also possible with a two pipe reverse return boiler water loop. Zoning will offer you savings on your heating bill. It does this by taking advantage of hydronic loop zoning and large pressure drop.
Conclusion | Boiler Water Loops
It should be noted that any piping system will be more efficient if the piping is insulated especially boiler piping.
Boiler Water Loops