Troubleshooting Broken Thermostats
The main connection between the air conditioning and heating system and the end user is the thermostat. Beyond the air conditioning and heating thermostat many people know nothing about their systems that keep them comfortable year round. There comes a time when the thermostat has a problem or the end user wants to replace the thermostat because they think it is a broken thermostat. It is not uncommon for a person to call an HVAC contractor and tell the secretary that they think the thermostat is broken because their air conditioner or heating system does not work. In some instances this is the case while in others the thermostat is not broken but something is wrong with the air conditioning and heating equipment that needs to be repaired. In either case it is usually best to call an HVAC professional to look at the problem especially if you want to replace the thermostat. There are a few things you can check with your thermostat before you call an HVAC professional. A little thermostat troubleshooting is in order.
What To Check for Troubleshooting the Thermostat - Troubleshooting Broken Thermostats
- An air conditioning and heating thermostat, even if it is a digital thermostat, is simply a temperature switch that turns the air conditioning and heating system on and off. As with any switch it needs electricity to function or cause a function with the air conditioning and heating equipment. Most residential and light commercial thermostats are powered by 24 volts A.C. The thermostat gets this 24 volts A.C. from the air conditioning and heating equipment. Usually this power comes from an air handler in an air conditioning and heating split system and from the main unit for air conditioning and heating package systems. Check the circuit breaker for the air handler to make sure it is not tripped. Also check the power switch which should be located near the air handling unit. It is not uncommon for people to mistake these switches for a light switch and turn them off. They unknowingly just turned the power off for their air conditioning and heating equipment including their thermostat. That is when they begin to think they have a broken thermostat. If you have a digital thermostat the power display and the thermostat power display light may not function if you have this problem. Some air conditioning and heating thermostats use batteries to power the back light which takes us to number two in air conditioning and heating thermostat troubleshooting. Check the power switch and breaker to ensure the power is on before assuming you have a broken thermostat
- The back display light for the digital thermostat does not function but the air conditioning and heating system works fine. Check the batteries as some digital thermostats require AA or AAA batteries for the back light to function on the thermostat. There are two main types of digital thermostats; Digital thermostats that use batteries for the back light to function and digital thermostats that use the power from the air conditioning and heating equipment. If you don’t know which kind of air conditioning and heating thermostat you have then open the thermostat up and look inside. If you don’t see any batteries or a battery compartment inside the thermostat then your thermostat uses power stealing technology. It is probably an older model digital thermostat and if it is a programmable thermostat then every time you lose power you will lose the program inside which takes us to the next step in air conditioning and heating thermostat troubleshooting.
- The programmable thermostat is always losing its program. This is most likely one of the older thermostats that use the power from the air conditioning and heating equipment and every time you lose power you lose the program inside the thermostat. Programming an air conditioning and heating programmable thermostat can be a chore for many people to figure out so a problem like this can be frustrating especially if you live in an area where there are constant power failures. The only solution to this problem is to replace the programmable thermostat with one that uses power stealing technology (it uses power from your air conditioning and heating system to hold the programs) and has a battery back-up just in case you lose power. This can save you lots of trouble and frustration in the long run keeping you from reprogramming the thermostat over and over again when power failures occur.
If the problem is persistent with the thermostat it is important get back to thermostat basics.
Troubleshooting Broken Thermostats - Thermostat Troubleshooting Basics
- Is the thermostat installed in the proper location. This is very important as a thermostat installed on a wall that has high heat gain or heat loss will never offer you comfort as it will react mostly to the temperature of the wall and not the air in the living space. Additionally, thermostats installed where direct sunlight can hit the thermostat is going to be a problem also. A thermostat located near an outside door or window will be affected every time the door or window is opened or closed. A thermostat should be located close to the return (where the filter is installed) so that it sense and reacts to the air returning to the air handler for conditioning. Additionally, thermostats located near heat sources like hot or cold water pipes, radiant heaters, fireplaces, electrical devices which produce heat, etc… will never offer accurate temperatures and conditioning for the space.
- Is there a big hole behind the thermostat that will feed cool or warm drafts to the back of the thermostat? All thermostats have a hole behind them where the wires come into the thermostat from the air handling unit. Check this and if you find a big hole behind the thermostat stuff some insulation in this hole and cover it with a piece of tape. This will prevent drafts from affecting the thermostat.
- Has the heating anticipator been properly set by a qualified air conditioning and heating technician? The heat anticipator is on mechanical non-digital thermostats and needs to be set according to the amp draw on the heating control circuit. The heat anticipator offers a small amount of energy savings and prevents thermostat overshooting for you as it shuts off the main burners because the fan will continue to run and dissipate the heat which remains in the furnace or heat. Digital and programmable thermostats have built in heating and cooling anticipators which automatically set themselves with no manual adjustments. The mechanical thermostat needs a manual adjustment and you need a tool called an amp meter to determine the proper setting. The cooling anticipator in the mechanical thermostat requires no manual adjustment.
- If you have a mechanical thermostat with a mercury bulb switching mechanism inside it this thermostat needs to be level. If the thermostat is not level you never get an accurate temperature in the residence or business.
Other problems that can occur with your air conditioning and heating thermostat need to be discussed with an HVAC professional as these problems can be technical and require special tools to fix. It is always a wise choice to call in an HVAC professional when you have problems with your air conditioning and heating equipment including your air conditioning and heating thermostat.
Troubleshooting Broken Thermostats