Air Handler Water Coil Freeze Stat - The HVAC Air Handler Freeze Stat is a low-temperature limit control and it is used mainly in commercial systems in the duct work on economizers or in air handlers just before any coil especially water coils. It is a safety and protection control to prevent extremely cold air from reaching the hot water or chilled water coils inside the air handler where the air enters from the economizer. (more…)
HVAC Enthalpy & Heat
Energy Recovery Wheels | HVAC Enthalpy & Heat - As the cost of energy rises engineers are looking for ways to improve and increase energy efficiency. Aside from HVAC equipment with higher energy efficiency rates, improving structures for less heat loss and heat gain, and building automation systems giving the equipment precision control for better efficiency of the equipment, there are other ways to increase energy efficiency inside buildings. One of the ways to increase energy efficiency inside buildings is to add energy recovery wheels to the economizer systems. A US Department of Energy study concluded energy recovery wheels can save over 15% of the energy used in commercial HVAC applications.
Hot Water Boiler Economizer PreHeater | Energy Efficiency
This is a hot water economizer and is a big preheater for domestic hot water use. This boiler plant serves a large community for heating and domestic hot water use. Domestic hot water is used for showers, washing dishes, laundry, ect, ect, ect…. The cold water supply from the city is routed through the economizer to be pre-heated before it goes through a heat exchanger and then the hot water storage tank. This system saves money because it uses the exhaust gases from the boiler to pre-heat the city water supply which is normally 50 degrees Fahrenheit. The exhaust gases from the boiler would otherwise be vented to the atmosphere and would be considered wasted heat. (more…)
Air Handler Return Dampers | HVAC Components - These return air dampers serve a large air handler on a rooftop. This return air damper ends up in a mixing box inside the air handler where the return air from the building mixes with the outside air from the economizer. (more…)
HVAC Damper Actuator for Economizer Free Cooling
This damper actuator controls a free cooling damper for an economizer. It is part of an economizer damper system which allows free outside air cooling when the outside air temperature and humidity are ideal. In the Fall and the Spring when the outside air temperatures are mild it is unnecessary to run the air conditioning system to cool the building if the system is set up for free cooling. The air conditioning system has duct work running to the outside. When the control system program calls for free cooling the outside air damper opens and the system draws in cool air from the outside. Another damper directs the return air, which originates inside the spaces of the building, to the outside. This brings cool conditioned air into the building while exhausting the warmer air to the outside. Another action that the control program initiates is the lockout of the air conditioner or mechanical cooling.
Free Cooling Air Conditioning - I’m looking for residential high performance system that uses air intake damper or a multistage (multi-zone) heating and cooling system similar to what I found at Economizer Systems and HVAC Control ?
Any suggestions? Answer…………… (more…)